IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. INTERNATIONAL. IEC is not a mandatory standard but provides information, guidance, and recommendations for the selection and application of. IEC Edition INTERNATIONAL. STANDARD. Surge arresters –. Part 5: Selection and application recommendations. IE. C. 9. –
|Published (Last):||9 April 2007|
|PDF File Size:||8.52 Mb|
|ePub File Size:||3.95 Mb|
|Price:||Free* [*Free Regsitration Required]|
Low-voltage limiters are covered under Clause 7. A list of standard insulation levels, based on the voltage stress to which the equipment is IEEE C Computational guide to insulation co-ordination and modeling of electrical iwc This technical report gives guidance on conducting insulation co-ordination studies which propose internationally recognized recommendations for the numerical modeling of electrical systems including arresters and for the implementation of deterministic and probabilistic methods adapted to the use of numerical programs.
Its object is to give information in terms of methods, modeling and examples, allowing for the application of the approaches presented in IECand for the selection of insulation levels of equipment or installations, as defined in IEC The way these transmission-line choices will improve or degrade lightning performance is also provided.
Insulation Coordination Standards Insulation co-ordination – Part 1: Read more about SIS Subscriptions. While some parameters such as voltage, routing, and capacity may be predetermined, other decisions are made at the discretion of the designer.
Definitions, principles and rules This part of IEC applies to three-phase a. The designer may exercise control over structure material and geometry, shielding if anyamount of insulation, grounding, and placement of arresters.
IEC | IEC Webstore
The faster, easier way to uec with standards. Please note that the selected standard is invalid. More complex and special solutions requiring study by experienced engineers is described, but specific solutions are not always given. This guide recognizes that a perfect line design does not exist, and that a series of compromises are made in any distribution-line design.
BS EN – Surge arresters. Selection and application recommendations
This standard is not maintained and applies to products not manufactured any longer. Accept and continue Learn more about the cookies we use and how to change your settings. This new edition covers new mechanical test requirements for polymer and porcelain housed arresters. See Complete Overview C Selection and application recommendations Status: Worldwide Standards We can source any standard from anywhere in the world. Preview Insulation co-ordination – Part 2: This association is for insulation co-ordination purposes only.
Also includes details of pollutant compositions and methods of application and the procedures associated with each mode of pollution. The guide 600999-5 not cover motors applied iev solid-state switched adjustable speed drives.
Surge arrester residual voltage is a major parameter to which most users have paid a lot of attention to when selecting the type and rating. Where technical information is not readily available, guidance is provided to aid toward proper surge protection and ief reduce interference to communication, control, and protection circuits due to surges and other overvoltages. IEEE IEEE Standard for Series Capacitors in Power Systems 60909-5 and assemblies of capacitors, insulation means, switching, protective equipment, and control accessories that form a complete bank for inserting in series with a transmission line are applied.
Related publications IEC Metal-oxide surge arresters without gaps for a. Sustainable Development Goals and standardisation, how do they connect?
This edition constitutes a technical revision. Though it will be many years before the both standards are virtually the same, this is a first step.
The protective equipment is mentioned in clauses 1. 660099-5
Selection and application recommendations Status: An additional section discusses uec special methods that may be used to improve lightning performance. This guide gives methods for insulation coordination of different air-insulated systems like transmission lines and substations.
Surge arresters – Part 5: Selection and application recommendations
The user of surge arresters will, in that case, not be required to apply the whole process introduced here to any new installation and the selection of 60099–5 resulting from prior practice may be continued. This edition includes the following significant technical changes with respect to the previous edition regarding the new surge arrester classification introduced in IEC Selection and application recommendations Article no: This standard applies to devices for separate mounting and to devices supplied 600999-5 with other equipment.
IEC Surge arresters – Part 3: Your basket is empty. Surge protective devices connected to telecommunications and signalling networks – Performance requirements and testing methods.
Report error on page. Surge arresters and low-voltage limiters for specific use in d. Surge Arresters and subcommittees 37A: